Tired of paying too much to replace just a motor or a relay or other HVACR parts? Need help on finding replacement parts? Got some HVACR questions and need advices? We specialize in Carrier, Bryant, Payne, York, Trane and Goodman air conditioner parts as well as refrigeration parts. Leave a comment, ask a question or just say hi. Parts are available to order on our website at www.gsistore.com
Wednesday, June 26, 2013
HVAC Troubleshooting Question
Recently we had responded to a question in one of the HVAC DIY forums. We like to share it here so our readers can read about it and learn something. Below is a portion of the message. "I started troubleshooting by making sure the condensate drain switch wasn't the issue and then did some tests with my multimeter. On the board I got 27ish volts across the heat, cooling, and fan terminals. At the t-stat I got... nothing. No reading at all on any of them. I jumpered R to Y on the board and everything runs just fine. House cooled down great. Jumpering at the t-stat wires didn't help anything. I've also swapped the board out with one I purchased at the recommendation of a service tech... there was no problem with the old board and it behaves the same way with both boards." In other words, the unit will not run at all when the writer jumps or hardwired R to Y at the thermostat but it runs just fine when he jumps it at the control board inside the furnace. Usually when something like this happen you want to check for loose wire or broken wire which breaks the 24V signal between the control board and the thermostat. This is exactly what happened in his case and all he had to do is just run a new set of wires. By knowing how the control works and by reading the control diagram of your a/c system you can easily troubleshoot thermostats, control boards and figure out which part might be wrong. Of course you should always let the professional handle it if you have any doubts but knowing a little about stuff like this can actually help you communicate with the pros. It is pretty fun to troubleshoot this kind of things especially when you found and fixed the bug.
Subscribe to: Post Comments (Atom)
I am very happy to say that this is an interesting post. I learned new information from your article, you are doing a great job. Thanks for sharing this kind of blog. toledo hvac companies
You are providing good knowledge. It is really helpful and factual information for us and everyone to increase knowledge. about hvac repair service .Continue sharing your data. Thank you.
This characteristic accelerates betting for everybody and makes extra advanced betting really simple. A player’s favorite bets can be found on any Roulette desk that means that players can place their saved bets time and time once more, at whichever desk they're playing in}. Offering final word|the final word} VIP stay gaming expertise on-line, our Salon Privé is a super-elegant, top-end VIP environment. Here your most discerning, high-wagering players can get pleasure from the perfect in stay gaming with high maximum bets and 텐벳 enhanced management at one-to-one, single-player private tables. Whether you want to apply earlier than playing in} actual money roulette, or just get pleasure from playing in} for enjoyable, free on-line roulette is a great way|a good way|an efficient way} to turn into a part of} the motion. You’ll find both basic and different roulette variations, so pick one that appeals and play free roulette now.
Post a Comment